If you don't get an e-mail with your access data please make sure that you have already registered with us. As soon as you are registered, you can login with your e-mail address and your password.
In case you still have problems loging in please turn to us by e-mail: firstname.lastname@example.org
rated current of 40A
rated currents of 30 mA differential
Short-circuit strength 10000A
rated voltage of 230/400V, 50Hz
A Residual Current Device is a generic term covering both RCCBs and RCBOs.
A Residual-Current Circuit Breaker (RCCB) is an electrical wiring device that disconnects a circuit whenever it detects that the electric current is not balanced between the energized conductor and the return neutral conductor. Such an imbalance may indicate current leakage through the body of a person who is grounded and accidentally touching the energized part of the circuit. A lethal shock can result from these conditions. RCCBs are designed to disconnect quickly enough to prevent injury caused by such shocks. They are not intended to provide protection against overcurrent (overload) or short-circuit conditions.
In the United States and Canada, a residual current device is most commonly known as a ground fault circuit interrupter (GFCI), ground fault interrupter (GFI) or an appliance leakage current interrupter (ALCI). In Australia they are sometimes known as "safety switches" or simply "RCD" and in the United Kingdom, along with circuit breakers, they can be referred to as "trips" or "trip switches".
A Residual Current Circuit Breaker with Overload protection (RCBO) combines the functions of overcurrent protection and leakage detection. An earth leakage circuit breaker (ELCB) may be a residual-current device, although an older type of voltage-operated earth leakage circuit breaker exists.
We are happy to inform you about a price change of this product respectively when it hits the price you want to purchase.